Customer name: Mary
Job location: Caroline Springs, VIC, 3023
Date required: ASAP. This job is urgent.
A/C type: Heating and cooling.
A/C install or repair: This is a heater repair job.
Job type: This is a residential job.
Mary's comments: AAPAC ducted heater not working and Lo error code on controller
Tested resistance on pressure switches
Found low pressure switch has tripped
Tested refrigerant levels
no refrigerant in system
Looks like leak around condenser or pipe after revering valve feeding condenser
Leak will need to be located correctly with nitrogen and Reg as of r22 refrigerant of 5.2kg
Filter dyrer will need to be replaced while repair is done
Repair will need to be done by a refrigeration mechanic