Hi, I have a double story rental house in Bankstown. Recently the A/C broke down. Had another technician had a look and provided an assessment (see screenshot below). I'd like to get a second opinion from an honest and reliable person. Please quote for the total repair cost or call out fee if a site visit is needed.
Unit: ActronAir (M Series) installed in 2008
Please email or SMS, no call, thanks.
Below is from another technician:
Inspected Actron ducted and found controls circuit breaker tripped. Rest and found system ran for a few minutes and then tripped again. Rest and tested for faults. Found mains for AC tripped. Diagonsed faulty indoor fan motor and indoor PCB. Fault is due to lack of maintenance and bloced return air filter.
Quote to replace indoor fan motor, barrels & deck complete, also to replace indoor PCB.
Specific Job Details:
Schedule: Need job done this week
Budget: Not Specified
Site Visit: Anytime